Fitness Center Energy Saving Equipment at Virgin Active - 4 months payback.
Annual Savings Achieved
- 6.8 tons CO2
- 5,571 kW/h site
- 12,620 kW/h inc transmission
- 4 Months
- Removal of reactive power charges
- Reduction of 77 amps per phase
- Reduction of 55 kVa demand
- Improved utility
Virgin Active are proud of their efficiency achievements and fitness center energy savings on each of their sites. They are also engaged with the Carbon Trust to improve efficiency even further.
The Carbon Trust identified power factor correction as a proven energy saving technology to improve electrical efficiency and remove penalties from the electricity bills and although Power Factor Correction had been installed many years ago, the system was non functional and now underrated for their present operation.
We carried out a combination of repairs and modifications to the old existing equipment resulting in an ROI of less than four months, returned carbon savings of 6.8 tons per annum and achieve and overall electrical efficiency of around 99% from a poor 80% before correction.
For more information on how EnergyAce can benefit your organisation, call us now on 01695 559785 or email email@example.com.Download Case Study
- Free Survey & Advice
- Guaranteed Savings
- Remove Reactive Charges
- Protect Appliances
- Reduce Maintenance Cost
- Reduce Max Demand
- Reduce Carbon Emissions
- Flexibility in Design & Build
+44 (0)1695 559785
Please fill in the details above and we'll get back to you
for a Free Survey
Subscribe to the LATEST NEWS from EnergyAce
Keep in touch and find out whats going on with EnergyAce by signing up to our newsletter.